As per NFPA 13 2013, 18.104.22.168 "exception" one can design to Ordinary Hazard 2 for powder coating but does not get into the ductwork portion of the design . I would imaging the 30gpm/15 psi would still apply but seems to defeat the purpose of the exception.
Also - I see that some treat the ductwork/stack 12'-0" max spacing run on the horizontal only. I interpret otherwise. Am I missing something?
Red Flag Submitted
Thank you for helping keep Eng-Tips Forums free from inappropriate posts. The Eng-Tips staff will check this out and take appropriate action.
Reply To This Thread
Posting in the Eng-Tips forums is a member-only feature.