The rooftop package unit is serving to a large office with two external walls with windows, the entrance lobby and an internal office space for which walls are not exposed. The thermostat is located in the large open office which is quickly achieving set point temperature in summer and cutting off the compressor and internal office and entrance lobby is not achieving desired set point temperature because thermostat is cutting of the compressors as soon as large open office is achieving the desired set point temperature and we are receiving complains. To overcome this problem, I have suggested to relocate the thermostat sensor inside the main return duct.
Did anybody came across similar situation. Can we resolve this problem by relocating the sensor inside the main return air duct. please advise.
Red Flag Submitted
Thank you for helping keep Eng-Tips Forums free from inappropriate posts. The Eng-Tips staff will check this out and take appropriate action.
Reply To This Thread
Posting in the Eng-Tips forums is a member-only feature.
When was the last time you drove down the highway without seeing a commercial truck hauling goods?The ubiquity of these machines underscores the important roll they play in modern commerce. Download Now