I'm going to design a water pipe system onsite fire hydrants for our project site and it requires a booster pump to meet a minimum 20 psi on the pipe system. I'm using waterCAD for analyzing the pipe system. Everytime I run it, it gives me a warning that -20 psi gage pressure on the suction side of the pump and pipe junction upstream or on the side of the pump. The same junction has a positive available pressure, although not enough, when the system is analyzed without the pump. Is the -20 psi gage pressure theoretically caused by the impeller? Is the positive pressure analyzed without the pump (which is gage pressure minus pressure loss due to friction) what I should account for the Net Positive Suction Head Available NPSH (A)? Or Is it the -20 psi gage pressure? Thanks in advance.
Red Flag Submitted
Thank you for helping keep Eng-Tips Forums free from inappropriate posts. The Eng-Tips staff will check this out and take appropriate action.
Reply To This Thread
Posting in the Eng-Tips forums is a member-only feature.
Since the later 1980s, manufacturing companies have seen over 3 percent in labor output year on year, with most of this productivty enhancement occuring because of the optimization of repetitive tasks. Download Now