Hello, I am working on an R.O. project and I have a question regarding the location of pressurized water (80 PSI) piping NEXT TO 480 volt electrical panels. I understand the "NO-NO" of installing water piping above panels and the obvious "nothing 36 inches in front of panels" rule. However, there is an argument as to the "next to" ruling. Could someone please help me out on this? Thanks!
Red Flag Submitted
Thank you for helping keep Eng-Tips Forums free from inappropriate posts. The Eng-Tips staff will check this out and take appropriate action.
Reply To This Thread
Posting in the Eng-Tips forums is a member-only feature.
When was the last time you drove down the highway without seeing a commercial truck hauling goods?The ubiquity of these machines underscores the important roll they play in modern commerce. Download Now