Hello guys....I have two questions....
1. Can fire dampers be placed on Fire rated bulk head openings?
2. Which code specify which all shaft or duct needs to be fire rated/ fire wall or it is upto the designers choice?
Red Flag Submitted
Thank you for helping keep Eng-Tips Forums free from inappropriate posts. The Eng-Tips staff will check this out and take appropriate action.
Reply To This Thread
Posting in the Eng-Tips forums is a member-only feature.
By implementing a new 3D CAD tool, top-performing manufacturers can reduce their development time by 19 percent and development costs by 15 percent. Most importantly, engineers can increase iterations by 14 percent â€” leading to more innovation and competitive advantages. Download Now