×
INTELLIGENT WORK FORUMS
FOR ENGINEERING PROFESSIONALS

Are you an
Engineering professional?
Join Eng-Tips Forums!
• Talk With Other Members
• Be Notified Of Responses
• Keyword Search
Favorite Forums
• Automated Signatures
• Best Of All, It's Free!

*Eng-Tips's functionality depends on members receiving e-mail. By joining you are opting in to receive e-mail.

Posting Guidelines

Promoting, selling, recruiting, coursework and thesis posting is forbidden.

New user to EPANET

New user to EPANET

(OP)
Hi,

I'm new to the forum and EPANET as well. I need to do a fire flow analysis for a relatively short line of 8" PVC that will have 2 new fire hydrants connected to an existing system. I don't have static pressure information for the existing hydrant but the residual was measured at 103 psi, and the flow at 826.20 gpm. I am unsure about how to set up the initial conditions (at the existing) in my system, if it should be considered a tank or reservoir, and what inputs I should use to model the fire flow correctly. I will attach what I have thus far, and hopefully someone will have a good idea on how I should proceed. Thank you for your time!! (Sorry, I had to edit the attachment because I noticed the elevations were not added to the junctions.)

RE: New user to EPANET

You need the static pressure from the Flow Test to be able to model it. Essentially you will be modeling the existing system using a pump and reservoir to simulate the distribution system that's supplying the water. The pump curve is set using 3 data points: 1. Static Pressure at Q=0; 2. Residual Pressure at Q=Flow Test; and 3. Calculated available fire flow at the minimum allowed pressure (typically 20 psi) calculated as shown here:
http://www.hosemonster.com/blog/calculate-rated-ca...

Without the static pressure, you don't have 1 and can't calculate 3.

#

RE: New user to EPANET

(OP)

Red Flag This Post

Please let us know here why this post is inappropriate. Reasons such as off-topic, duplicates, flames, illegal, vulgar, or students posting their homework.

Red Flag Submitted

Thank you for helping keep Eng-Tips Forums free from inappropriate posts.
The Eng-Tips staff will check this out and take appropriate action.

Close Box

Join Eng-Tips® Today!

Join your peers on the Internet's largest technical engineering professional community.
It's easy to join and it's free.

Here's Why Members Love Eng-Tips Forums:

• Talk To Other Members
• Notification Of Responses To Questions
• Favorite Forums One Click Access
• Keyword Search Of All Posts, And More...

Register now while it's still free!