Rolled Carpet Storage Rolled Carpet Storage MFS0035 (Mechanical) (OP) 4 Sep 16 14:05 Is anyone aware of fire sprinkler design criteria for rack storage of rolled carpet other than FMDS0830? RE: Rolled Carpet Storage TravisMack (Mechanical) 4 Sep 16 16:06 It is outside the scope of NFPA 13 criteria. The only published info I am aware of is the FM data sheets. Travis Mack MFP Design, LLC www.mfpdesign.com "Follow" us at https://www.facebook.com/pages/MFP-Design-LLC/9221... RE: Rolled Carpet Storage stookeyfpe (Specifier/Regulator) 5 Sep 16 03:50 Travis is correct. I don't have access to GE GAP and that would be the only other source other than proprietary fire test data. RE: Rolled Carpet Storage NewtonFP (Automotive) 6 Sep 16 15:10 I had a project years ago with rack storage of rolled carpet but it was stored ~5'-10' or so. I think we used 0.6/2000 with K14 storage sprinklers. Higher than that and there isn't anything I'm aware of.