I hope this is question is not to simple, but where in IEC60364 is it required to break the neutral in addition to the live conductors in a TT supply? Where in the system should the neutral be interrupted when mandated?
Red Flag Submitted
Thank you for helping keep Eng-Tips Forums free from inappropriate posts. The Eng-Tips staff will check this out and take appropriate action.
Reply To This Thread
Posting in the Eng-Tips forums is a member-only feature.