We have on site a GE design 9A5 generator, brush less , with ORION journal bearings with pads. During operation it was triggered a high liquid level detection alarm. By opening the roof drain plug, we see a total drainage of 2 liters per day, with bearing lube oil flow at 18 liters per minute. We saw also oil on the air ducts of pilot exciter. Quick inspection done inside the windings from air leakage filters manhole did not reveal significant oil leaks, only oil droplets. Generator oil pressure is stable, lube oil tank level is stable, no abnormality is seen in vibrations, metal temperatures, oil drain temperatures. For sure there is no water leak from above installed coolers. Do you have any experience with oil leaks in this type of generator or similar? Thank you in advance.
Red Flag Submitted
Thank you for helping keep Eng-Tips Forums free from inappropriate posts. The Eng-Tips staff will check this out and take appropriate action.
Reply To This Thread
Posting in the Eng-Tips forums is a member-only feature.
Cities are ceaseless engines of engineering activity. Itâ€™s likely that while you were on your way to work, you encountered a number of infrastructure development projects under construction. Download Now
When was the last time you drove down the highway without seeing a commercial truck hauling goods?The ubiquity of these machines underscores the important roll they play in modern commerce. Download Now