Until now we have always build panels for our own equipment with predetermined motor loads. Now we are asked to build a UL508a panel to control lighting loads. The supply voltage, breakers, and lighting loads will be determined by the end user/installer. They are unknown to us. Is there a way to deal with UL 508a Section 52.2 and other sections that ask for the current and voltage of loads to be marked on the panel? Can the panel be labeled with the max amperage and type of load allowed by the contactor? The only control we have on the load is to say that it is limited by the size of the contactor.
Thanks for any help,
Red Flag Submitted
Thank you for helping keep Eng-Tips Forums free from inappropriate posts. The Eng-Tips staff will check this out and take appropriate action.
Reply To This Thread
Posting in the Eng-Tips forums is a member-only feature.
When was the last time you drove down the highway without seeing a commercial truck hauling goods?The ubiquity of these machines underscores the important roll they play in modern commerce. Download Now