Low pressure API tanks seldom have installed spare vent devices (PVRV, ERV, VRV, etc). How does your company handle maintenance and inspections of these devices when there isn't an installed spare? Do you do all of this testing/inspection in-situ, without removing the device to the shop? Do you remove the device and install a temporary shelter over the open tank nozzle while the device is in the shop? Does your company have a standard maintenance procedure for safely protecting the tank while these devices are removed for inspection?
Red Flag Submitted
Thank you for helping keep Eng-Tips Forums free from inappropriate posts. The Eng-Tips staff will check this out and take appropriate action.
Reply To This Thread
Posting in the Eng-Tips forums is a member-only feature.