We have approximately 1000' of 15" Sanitary line (upstream of a larger system) that we are discharging additional flows into. There is one small (100') section of pipe that is laid at .25 slope that is not adequate to handle the additional flow. Is it customary to upsize (pipe burst or open trench) just this one section of pipe in the middle of a 15" system? Or do would you want to upsize this run of pipe and all 15" downstream? You would not design anything like this but as a retrofit is this customary?
Red Flag Submitted
Thank you for helping keep Eng-Tips Forums free from inappropriate posts. The Eng-Tips staff will check this out and take appropriate action.
Reply To This Thread
Posting in the Eng-Tips forums is a member-only feature.
Managing reverse logistics and depot repair, or all operations related to the reuse of products and materials, is a growing challenge for B2C and B2B manufacturers, retailers and service organizations. Download Now