How does one calculate tank separation distances for groups of tanks larger than 2 x 2 in accordance with NFPA? Say if I have a grid of 3 x 3 storage tanks, all floating roof, all flammable for the sake of this question. Is it one uniform tank distance calculated by summing every possible adjacent tank diameter combinations and dividing by 6? It seems like the number will be excessively large if I follow the methodology as described for 2 tanks by 2 tanks as explained in the NFPA 30 handbook. Thank you for your assistance.
Red Flag Submitted
Thank you for helping keep Eng-Tips Forums free from inappropriate posts. The Eng-Tips staff will check this out and take appropriate action.
Reply To This Thread
Posting in the Eng-Tips forums is a member-only feature.
Cities are ceaseless engines of engineering activity. Itâ€™s likely that while you were on your way to work, you encountered a number of infrastructure development projects under construction. Download Now
When was the last time you drove down the highway without seeing a commercial truck hauling goods?The ubiquity of these machines underscores the important roll they play in modern commerce. Download Now