I was recently stumped by the following: consider a 800/400/1 Class P CT as per IEC 60044.1. The rated burden is given as 7.5VA (or 7.5ohms) at the 400/1 tap. At the 800/1 tap it is specified as 5P20. Is there a way of determing the rated burden on the 800/1 tap based on the information provided above?
Red Flag Submitted
Thank you for helping keep Eng-Tips Forums free from inappropriate posts. The Eng-Tips staff will check this out and take appropriate action.
Reply To This Thread
Posting in the Eng-Tips forums is a member-only feature.
ENGINEERING.com surveyed 364 product development professionals to glean insights into how their teams are performing today, and what technologies are most useful to support their processes. Download Now
3D printing has quickly expanded beyond the realm of prototyping and into the world of end part manufacturing. Desktop 3D printers need not be used for making parts themselves, but as a secondary process for producing tools. Download Now
Creating tooling for injection molding is an expensive and complex proposition. Until recently, the only way to avoid tooling defects causing air traps, voids, shrinkage and the like was to employ a time-consuming and tedious physical prototyping process. Download Now