I was recently stumped by the following: consider a 800/400/1 Class P CT as per IEC 60044.1. The rated burden is given as 7.5VA (or 7.5ohms) at the 400/1 tap. At the 800/1 tap it is specified as 5P20. Is there a way of determing the rated burden on the 800/1 tap based on the information provided above?
Red Flag Submitted
Thank you for helping keep Eng-Tips Forums free from inappropriate posts. The Eng-Tips staff will check this out and take appropriate action.
Reply To This Thread
Posting in the Eng-Tips forums is a member-only feature.
Current integrated circuit (IC) designs are complex, which can result in different voltages being located close to one another. To prevent time dependent dielectric breakdown (TTDB), it is essential to incorporate space rules within IC design. Download Now
3D printing offers the ability to manufacture complex geometries, custom components on-demand and batches of short-run parts. However, with a new fabrication method comes new design principles. Download Now