I was recently stumped by the following: consider a 800/400/1 Class P CT as per IEC 60044.1. The rated burden is given as 7.5VA (or 7.5ohms) at the 400/1 tap. At the 800/1 tap it is specified as 5P20. Is there a way of determing the rated burden on the 800/1 tap based on the information provided above?
Red Flag Submitted
Thank you for helping keep Eng-Tips Forums free from inappropriate posts. The Eng-Tips staff will check this out and take appropriate action.
Reply To This Thread
Posting in the Eng-Tips forums is a member-only feature.
Cities are ceaseless engines of engineering activity. Itâ€™s likely that while you were on your way to work, you encountered a number of infrastructure development projects under construction. Download Now
When was the last time you drove down the highway without seeing a commercial truck hauling goods?The ubiquity of these machines underscores the important roll they play in modern commerce. Download Now