ASCE 7 13.1.3 states the Component Importance Factor for life safety purposes including sprinkler systems shall have an Ip 0f 1.5. I am requesting the contractor to follow chapter 9 on the NFPA 13. The contractor stated no seicmic is required for a seismic design catagory B. It is my understanding of the ASCE 7 13.1.3 because it's a sprinkler system it's not exempted. I am new to inspecting in Texas and was told an engineer is not required to sign off on the sprinkler drawing as they were in S.C. so I have no one to question other than the contractor which has a Fire Protection Specialist performing the drawing.
Red Flag Submitted
Thank you for helping keep Eng-Tips Forums free from inappropriate posts. The Eng-Tips staff will check this out and take appropriate action.
Reply To This Thread
Posting in the Eng-Tips forums is a member-only feature.
Combining the Internet of Things (IoT) with augmented reality (AR) could have unprecedented effects on industry, giving people the ability to harness devices for entirely new capabilities. Download Now