ASCE 7 13.1.3 states the Component Importance Factor for life safety purposes including sprinkler systems shall have an Ip 0f 1.5. I am requesting the contractor to follow chapter 9 on the NFPA 13. The contractor stated no seicmic is required for a seismic design catagory B. It is my understanding of the ASCE 7 13.1.3 because it's a sprinkler system it's not exempted. I am new to inspecting in Texas and was told an engineer is not required to sign off on the sprinkler drawing as they were in S.C. so I have no one to question other than the contractor which has a Fire Protection Specialist performing the drawing.
Red Flag Submitted
Thank you for helping keep Eng-Tips Forums free from inappropriate posts. The Eng-Tips staff will check this out and take appropriate action.
Reply To This Thread
Posting in the Eng-Tips forums is a member-only feature.
The automotive parts aftermarket is a 2 trillion-dollar business. Major OEMâ€™s like General Motors are eager to win a substantial portion of that market in one of the most difficult supply chain systems in the world. Download Now
Designers in every industry are being pushed to produce larger and more complex product assembles. Add to that the demands that new software features place on your hardware, and you can be in for some serious performance issues. Download Now