Can anyone explain to me how vertical forces due to seismic loading are accounted for in the load combination in this publication? I am familiar with the IBC provisions of 0.2*Sds*D and applying this term with the dead load factor. However, since the load combinations in this ASCE publications are different, and there is no mention of how to apply vertical seismic loads, I am not sure the correct way to apply the seismic load when modeling substation structures use this publication.
Red Flag Submitted
Thank you for helping keep Eng-Tips Forums free from inappropriate posts. The Eng-Tips staff will check this out and take appropriate action.
Reply To This Thread
Posting in the Eng-Tips forums is a member-only feature.
Cities are ceaseless engines of engineering activity. Itâ€™s likely that while you were on your way to work, you encountered a number of infrastructure development projects under construction. Download Now
When was the last time you drove down the highway without seeing a commercial truck hauling goods?The ubiquity of these machines underscores the important roll they play in modern commerce. Download Now