What is the pressure drop calculation method for an exhaust ductwork system where multiple exhaust fans discharge into a common header, and the combined E/A duct run out the building? Can you assume the friction is the same as a single fan system? Also, how do you size the fan with the back pressure from the other fans?
Red Flag Submitted
Thank you for helping keep Eng-Tips Forums free from inappropriate posts. The Eng-Tips staff will check this out and take appropriate action.
Reply To This Thread
Posting in the Eng-Tips forums is a member-only feature.
Todayâ€™s product development cycle is fraught with difficulties. Increased demands for complex functionality and reduced product development windows cause engineering teams to borrow practices from the IT industry, swapping outdated serial workflows for a more flexible and collaborative design method known as Agile Product Engineering. Download Now
Version control is neither a new concept or a new software feature. But with the explosion of digital information, thereâ€™s an even greater need for tight control and management of documents and data. Download Now