I am designing a gravity flow system for a rural area. The elevation difference b/w the source and point of use is 1004 feet (306 m). I will provide a 1.5" Schedule 40 PVC pipe. I would like to know what is the ideal static pressure for pipe and fittings where I should locate a break pressure tank in the system. Also will pressure reducing valves serve the same purpose as break pressure tanks?
Red Flag Submitted
Thank you for helping keep Eng-Tips Forums free from inappropriate posts. The Eng-Tips staff will check this out and take appropriate action.
Reply To This Thread
Posting in the Eng-Tips forums is a member-only feature.
More and more manufacturers are getting into the Industrial Internet of things (IIoT). Those that succeed early in the IIoT arena can be leaders in their market, or solidify their position. Download Now