I am designing a gravity flow system for a rural area. The elevation difference b/w the source and point of use is 1004 feet (306 m). I will provide a 1.5" Schedule 40 PVC pipe. I would like to know what is the ideal static pressure for pipe and fittings where I should locate a break pressure tank in the system. Also will pressure reducing valves serve the same purpose as break pressure tanks?
Red Flag Submitted
Thank you for helping keep Eng-Tips Forums free from inappropriate posts. The Eng-Tips staff will check this out and take appropriate action.
Reply To This Thread
Posting in the Eng-Tips forums is a member-only feature.
As products become increasingly complex, product lifecycle management (PLM) is steadily growing, with new solutions and companies entering the space. However, businesses seeking to implement PLM may still face issues in managing products across entire lifecycles. Download Now