I am designing a gravity flow system for a rural area. The elevation difference b/w the source and point of use is 1004 feet (306 m). I will provide a 1.5" Schedule 40 PVC pipe. I would like to know what is the ideal static pressure for pipe and fittings where I should locate a break pressure tank in the system. Also will pressure reducing valves serve the same purpose as break pressure tanks?
Red Flag Submitted
Thank you for helping keep Eng-Tips Forums free from inappropriate posts. The Eng-Tips staff will check this out and take appropriate action.
Reply To This Thread
Posting in the Eng-Tips forums is a member-only feature.
Managing reverse logistics and depot repair, or all operations related to the reuse of products and materials, is a growing challenge for B2C and B2B manufacturers, retailers and service organizations. Download Now