## Maximum Flow through certain diameter of pipe?

## Maximum Flow through certain diameter of pipe?

(OP)

How would I go about determining the maximum amount of flow through a pipe of certain diameter within our distribution system?

The info I would have at hand would be pressure, diameter, pipe type, etc.

The info I would have at hand would be pressure, diameter, pipe type, etc.

## RE: Maximum Flow through certain diameter of pipe?

## RE: Maximum Flow through certain diameter of pipe?

Would a modeling system like EPAnet be a program to start with?

## RE: Maximum Flow through certain diameter of pipe?

## RE: Maximum Flow through certain diameter of pipe?

Is there a theoretical maximum for a 6" line with a certain amount of pressure?

## RE: Maximum Flow through certain diameter of pipe?

q=10.2*ID^2.5

Since it is an empirical equation it only makes sense if the ID is in inches.

Other than that, if you know the pressure in your 24" header, the length of the 6" and can estimate the backpressure caused by their end devices you can use D'Arcy-Weisbach. One version of that is:

q=(C*dP*ID*A^2/(L*ρ*f

_{m}))^0.5for FPS units:

"C" is 2*g

"f

_{m}" is the Moody friction factor (if you're not familiar with that term, then you need to get help)"dP" is in lbf/ft^2

"ID" is in ft

"A" is in ft^2

"ρ" is in lbm/ft^3

"L" is in ft

q works out to ft^3/sec

David

## RE: Maximum Flow through certain diameter of pipe?

However, as a rough estimate, the maximum velocity through the 6-Inch pipe is expected to be about 10 feet per second which gives you about 900 gallons per minute.

You can use the calculator in the link. The headloss from a 6-Inch pipe, 1000 feet long, 10 feet per second velocity is about 20 psi.

http://irr

## RE: Maximum Flow through certain diameter of pipe?

## RE: Maximum Flow through certain diameter of pipe?

bimr, how did you know that the flow can be expected to be around 10 ft/s? I'm familiar with the Hazen-Williams equation/nomograph but wasn't sure what velocity I should plug in

## RE: Maximum Flow through certain diameter of pipe?

City water mains are designed for 3-5 ft/sec.

## RE: Maximum Flow through certain diameter of pipe?

You are suppose to do the reverse calculation.

You have a X pressure in the 24 inch head.

You know the length of the 6 inch pipe, the material and the other properties of the water.

If at the end of the 6 inch pipe is open ended and not too many bend and turns,no major fitting that causes significant pressure /hea losses,just use the formula provided by Zdas04 and get the estimate flow rate.

Of cause you have to add or deduct the equivalent of the static height difference between the header and exit point of the 6 inch pipe in the value of the dp ( pressure in the header).

## RE: Maximum Flow through certain diameter of pipe?

In case of having enough data and your system is not too complicated (I mean there arent closed circles in that) maybe a simple Bernoulli equation can be a really useful help !

## RE: Maximum Flow through certain diameter of pipe?

Beyond this I will only caution that "C900" does not really nail down much the specific features of all pvc pipe that you may be dealing with. This specification has meant different things at different times, with regard to dimensions, thicknesses and/or pressure ratings etc. Again, searches will help in understanding this history. You will find also with web keyword search that in general many authorities are most unomfortable with high fluid flow velocities (as have been mentioned in this thread) and pvc piping in general, I suspect based on lessons, experience or other authoritative references.