Our isolation valves cannot fully stop the steam from getting to the steam turbine (combined cycle plant). At around 40psi, the MWs drop or jump by 10-20 MW within a second. I think it is a crack on the stem of the control valve. Could it be something else?
Is there anyway to fix this without doing a total plant outage?
Red Flag Submitted
Thank you for helping keep Eng-Tips Forums free from inappropriate posts. The Eng-Tips staff will check this out and take appropriate action.
Reply To This Thread
Posting in the Eng-Tips forums is a member-only feature.
Since the later 1980s, manufacturing companies have seen over 3 percent in labor output year on year, with most of this productivty enhancement occuring because of the optimization of repetitive tasks. Download Now