×
INTELLIGENT WORK FORUMS
FOR ENGINEERING PROFESSIONALS

Are you an
Engineering professional?
Join Eng-Tips Forums!
• Talk With Other Members
• Be Notified Of Responses
• Keyword Search
Favorite Forums
• Automated Signatures
• Best Of All, It's Free!

*Eng-Tips's functionality depends on members receiving e-mail. By joining you are opting in to receive e-mail.

#### Posting Guidelines

Promoting, selling, recruiting, coursework and thesis posting is forbidden.

# Parallel Generators Circulating Currents

## Parallel Generators Circulating Currents

(OP)
I am doing the electrical design for a project that consists of two 13.8 kV 1500kW co-gens, and one 13.8 kV 1100kW co-gen. All are set to be running in parallel with the utility on the same 13.8kV bus. I am trying to figure out what adverse effects would circulating neutral currents have on this system? Would having different impedances on the neutral ground resistors cause circulating neutral currents?

Thanks,

### RE: Parallel Generators Circulating Currents

No.

Bill
--------------------
"Why not the best?"
Jimmy Carter

### RE: Parallel Generators Circulating Currents

We had 3 generators we balanced onboard ship and we never had an issue with neutral current between generators. Once the frequencies were in sync and the load balanced between the generators they fed the load with no problems between them.

### RE: Parallel Generators Circulating Currents

I assume there isn't a neutral conductor as such, but an earthing resistor connecting the star point of each generator stator winding to earth. Circulating currents may cause problems with your earth fault protection, depending on how it is designed. From a purist's point of view it would be preferable use a transformer to isolate each generator from the load bus using a transformer and provide neutral earthing for the bus.

----------------------------------

If we learn from our mistakes I'm getting a great education!

### RE: Parallel Generators Circulating Currents

Differing harmonic voltages in the generators can cause circulating harmonic currents.  The main issue is generally the continuous rating of the grounding resistors.  The actual kW losses are pretty low, but the standard 10 second resistor no longer has a published continuous rating, at least in the ANSI world.

David Castor
www.cvoes.com

#### Red Flag This Post

Please let us know here why this post is inappropriate. Reasons such as off-topic, duplicates, flames, illegal, vulgar, or students posting their homework.

#### Red Flag Submitted

Thank you for helping keep Eng-Tips Forums free from inappropriate posts.
The Eng-Tips staff will check this out and take appropriate action.

Close Box

# Join Eng-Tips® Today!

Join your peers on the Internet's largest technical engineering professional community.
It's easy to join and it's free.

Here's Why Members Love Eng-Tips Forums:

• Talk To Other Members
• Notification Of Responses To Questions
• Favorite Forums One Click Access
• Keyword Search Of All Posts, And More...

Register now while it's still free!