I have two 1800 kVA emergency standby generators that can parallel the utility. When either engine, alone or in parallel, is in parallel with the utility, I have excessive amounts of third harmonic neutral current. This will cause the utility and generator breakers to trip on ground faults. I have verified that I have same pitch generators(11/16). I am concerned that my utility transformer is to blame. I currently have a 1500kVA wye-wye transformer with both the primary and secondary neutrals grounded. It has been a concern that the high side neutral should not be grounded. I am in the process of trying to have the Utility transformer changed to a 2500kVA delta-wye. Do you think this will help?
Red Flag Submitted
Thank you for helping keep Eng-Tips Forums free from inappropriate posts. The Eng-Tips staff will check this out and take appropriate action.
Reply To This Thread
Posting in the Eng-Tips forums is a member-only feature.
The automotive parts aftermarket is a 2 trillion-dollar business. Major OEMâ€™s like General Motors are eager to win a substantial portion of that market in one of the most difficult supply chain systems in the world. Download Now
Designers in every industry are being pushed to produce larger and more complex product assembles. Add to that the demands that new software features place on your hardware, and you can be in for some serious performance issues. Download Now