×
INTELLIGENT WORK FORUMS
FOR ENGINEERING PROFESSIONALS

Are you an
Engineering professional?
Join Eng-Tips Forums!
• Talk With Other Members
• Be Notified Of Responses
• Keyword Search
Favorite Forums
• Automated Signatures
• Best Of All, It's Free!

*Eng-Tips's functionality depends on members receiving e-mail. By joining you are opting in to receive e-mail.

#### Posting Guidelines

Promoting, selling, recruiting, coursework and thesis posting is forbidden.

# Vortex Breaker Design Guide

## Vortex Breaker Design Guide

(OP)
Hello,

I need to determine whether a 275 psig steam drum will require a vortex breaker at its bottom nozzle that goes to the suction of a pump. I have a 12" outlet nozzle and suction line to the pump. The flow rate is 1,600 gpm. Liquid level in the drum is about 5 ft above the bottome nozzle, and the bottom nozzle is 20 ft above the pump suction nozzle.

Can anyone share any guidelines/rules of thumbs/references for this?

David

### RE: Vortex Breaker Design Guide

I have heard and used the rule that submergence to avoid vortex problems should be at least 1 foot for each foot per second of velocity at the nozzle.  For your example, 1600 gpm passing into a 12" nozzle, you would have about 4.5 feet per second velocity entering the nozzle.  This assumes schedule 40 pipe.  Thus, you would want at least 4.5 feet of submergence.  That could be cutting it a little close.  I would consider adding a simple vortex breaker in case the flow could be a little higher than design or the level a little lower than design.

I found this same value (1 foot per foot per second) in Cameron Hydraulic Data related to submergence for side intake dry pit pumps.

Johnny Pellin

### RE: Vortex Breaker Design Guide

If I am lucky enough to be designing a new tank, not recycling an old one, I always put the vortex breakers in.  They are cheap insurance.

Regards
StoneCold

### RE: Vortex Breaker Design Guide

You can use the following equation from the ANSI/HI 9.8-1998 "Hydraulic Institute´s Pump Intake Design" that is:
S = D + 2.3DFr
S is the minimum required submergence to avoid vortex formation.
D is the nozzle diameter and Fr is the dimensionless Froud number, Fr = V/(gD)**0.5
V is the nozzle flow velocity and g the gravitational acceleration.

#### Red Flag This Post

Please let us know here why this post is inappropriate. Reasons such as off-topic, duplicates, flames, illegal, vulgar, or students posting their homework.

#### Red Flag Submitted

Thank you for helping keep Eng-Tips Forums free from inappropriate posts.
The Eng-Tips staff will check this out and take appropriate action.

Close Box

# Join Eng-Tips® Today!

Join your peers on the Internet's largest technical engineering professional community.
It's easy to join and it's free.

Here's Why Members Love Eng-Tips Forums:

• Talk To Other Members
• Notification Of Responses To Questions
• Favorite Forums One Click Access
• Keyword Search Of All Posts, And More...

Register now while it's still free!