I work in a shop where equipment is wired from a breaker panel to a local disconnect, 480vac 30 amp, then to the unit. The location of the disconnect is on the wall behind the machine. most of the machines are spaced 2 1/2 feet off the wall. Our in house safety person says that the expectation of clearance of a local disconnect is the same as the electrical panel that feeds it. I'm under the impression that clearance standards do not apply to local disconnects. We are starting a VPP program here and an OSHA inspector will be out to evaluate our site. My question is, do I need to have the electrical panel clearance at each local disconnect. We have a great deal more on conveyor motors and lifts. Which are near or at the motor, and depending on the motor location, not always readily accessable. Thanks, Mike
Red Flag Submitted
Thank you for helping keep Eng-Tips Forums free from inappropriate posts. The Eng-Tips staff will check this out and take appropriate action.
Reply To This Thread
Posting in the Eng-Tips forums is a member-only feature.
Virtual reality (VR) has been around longer than you might think—more than half a century—but it’s only in the last few years that we’ve seen companies and researchers explore its practical applications for manufacturing. Download Now