Just wondering, is it exceptable to use a density of .05 gpm to design for a NFPA 13R Light Hazard only? I am reviewing a set of plans and am not used to seeing that low of a density. Any comments would be helpful. Thanks.
Red Flag Submitted
Thank you for helping keep Eng-Tips Forums free from inappropriate posts. The Eng-Tips staff will check this out and take appropriate action.
Reply To This Thread
Posting in the Eng-Tips forums is a member-only feature.
Managing reverse logistics and depot repair, or all operations related to the reuse of products and materials, is a growing challenge for B2C and B2B manufacturers, retailers and service organizations. Download Now