I am looking to replace 3/4" and 1" schedule 80 and schedule 40, in both sizes, and wanted to know if there is a definite standard as to when you can and cannot use unions on certain size pipe. Steam pressure can range from 60 - 100 psi.
Red Flag Submitted
Thank you for helping keep Eng-Tips Forums free from inappropriate posts. The Eng-Tips staff will check this out and take appropriate action.
Reply To This Thread
Posting in the Eng-Tips forums is a member-only feature.