I would appreciate hearing from anyone that has had experience in storage tank settlements, both uniformly & differentially.API 650 doesn't address this very much that I can find other than:Par. 126.96.36.199 d. "The columns shall be effectively....in the event of vertical movement of the columns relative to tank bottom of up to 3 in.".Par. 188.8.131.52 (hydro test)"...differential settlement greater than 1/2" per 32 ft. of circumference or uniform settlement of 2 in."......Neither of these paragraphs address differential settlement across the tank bottom. Other paragraphs refer to "excessive" settlement without defining what is meant by "excessive".Case in point - I am designing a tank that is 100' Dia. x 64' Shell Height, 1% bottom crown up from center to outer shell. Single center column-supported roof with rafters.Geotech report says I can expect settlement of 8.4" at edge and 15" at center of tank which equates to differential settlement of 6.6" Question: do I take the 3" vertical movement of "up to 3" mentioned in Par. 184.108.40.206 d, as the max. differential allowable or am I missing something here?Any thoughts, suggestions, past experience, etc. would be really appreciated.I realize that API 653 has some guidelines but this is a new tank and thus API 653 does not apply. Any other industry standards that would apply?
Red Flag Submitted
Thank you for helping keep Eng-Tips Forums free from inappropriate posts. The Eng-Tips staff will check this out and take appropriate action.
Reply To This Thread
Posting in the Eng-Tips forums is a member-only feature.
There is proven benefit for product development teams in using an integrated design and data management system.
However, not all product teams can afford, need or want all the various modules in an enterprise PLM system.
Rapid prototyping has become a game-changing innovation for designers, engineers and manufacturers. Previously, the process of creating wood or metal prototypes took weeks or months and the cost was often so prohibitive that designers skipped prototypes entirely and went directly from CAD to tooling. Download Now