I would appreciate hearing from anyone that has had experience in storage tank settlements, both uniformly & differentially.API 650 doesn't address this very much that I can find other than:Par. 126.96.36.199 d. "The columns shall be effectively....in the event of vertical movement of the columns relative to tank bottom of up to 3 in.".Par. 188.8.131.52 (hydro test)"...differential settlement greater than 1/2" per 32 ft. of circumference or uniform settlement of 2 in."......Neither of these paragraphs address differential settlement across the tank bottom. Other paragraphs refer to "excessive" settlement without defining what is meant by "excessive".Case in point - I am designing a tank that is 100' Dia. x 64' Shell Height, 1% bottom crown up from center to outer shell. Single center column-supported roof with rafters.Geotech report says I can expect settlement of 8.4" at edge and 15" at center of tank which equates to differential settlement of 6.6" Question: do I take the 3" vertical movement of "up to 3" mentioned in Par. 184.108.40.206 d, as the max. differential allowable or am I missing something here?Any thoughts, suggestions, past experience, etc. would be really appreciated.I realize that API 653 has some guidelines but this is a new tank and thus API 653 does not apply. Any other industry standards that would apply?
Red Flag Submitted
Thank you for helping keep Eng-Tips Forums free from inappropriate posts. The Eng-Tips staff will check this out and take appropriate action.
Reply To This Thread
Posting in the Eng-Tips forums is a member-only feature.
3D printing has opened new doors to rapid prototyping and even rapid production, providing users with the unprecedented ability to visualize products before mass manufacturing and create new designs that could not be made by any other method. Download Now
Ensuring that product lifecycle stakeholders throughout your organization can access the most accurate, up-to-date product information will benefit all aspects of both the product and the organization itself. Download Now
Since the IEEE 802.3bj 100 Gb/s Backplane Ethernet standard has been officially approved, Channel Operating Margin (COM) will likely become an important quality-evaluation method for SERDES links. Download Now