For the 750/1 CT in the CT burden Test We are injecting 1 Ampere in the CT secondary & the reading in Relay for that phase Shows 750A, the voltage measured at the Secondary terminals is 2 Volts. So the Burden measured is 2 VA. the CT Name plate mentions 15 VA. Is this type of Testing sufficient for CT burden Test.
Red Flag Submitted
Thank you for helping keep Eng-Tips Forums free from inappropriate posts. The Eng-Tips staff will check this out and take appropriate action.
Reply To This Thread
Posting in the Eng-Tips forums is a member-only feature.
Todayâ€™s product development cycle is fraught with difficulties. Increased demands for complex functionality and reduced product development windows cause engineering teams to borrow practices from the IT industry, swapping outdated serial workflows for a more flexible and collaborative design method known as Agile Product Engineering. Download Now
Version control is neither a new concept or a new software feature. But with the explosion of digital information, thereâ€™s an even greater need for tight control and management of documents and data. Download Now