For the 750/1 CT in the CT burden Test We are injecting 1 Ampere in the CT secondary & the reading in Relay for that phase Shows 750A, the voltage measured at the Secondary terminals is 2 Volts. So the Burden measured is 2 VA. the CT Name plate mentions 15 VA. Is this type of Testing sufficient for CT burden Test.
Red Flag Submitted
Thank you for helping keep Eng-Tips Forums free from inappropriate posts. The Eng-Tips staff will check this out and take appropriate action.
Reply To This Thread
Posting in the Eng-Tips forums is a member-only feature.
Over the past few years, there has been growing interest among industrial companies and solutions providers with regards to Product Innovation Platforms, where design, manufacturing and IoT tools are bundled into a single software package. Download Now
Over the last 25 years, digital technologies have fundamentally transformed nearly every aspect of modern life. This transformation is ongoing, and itâ€™s occurring at an ever-quickening pace. Download Now