I am working on a warehouse that will have a battery charging station in it, and I will need to provide exhaust. I have found information on battery charging rooms talking about number of air changes per hour, but since this is just a small corner space of the whole warehouse, that doesn't really apply. I also saw where ASHRAE 62 calls for 1 CFM/charging ampere. The IMC just calls for ventilation as required.
I was thinking about installing a hood of some sort with a flow rate determined by using the 1 cfm/charging ampere. There will be an explosion proof fan on the roof. Any other ideas?
Red Flag Submitted
Thank you for helping keep Eng-Tips Forums free from inappropriate posts. The Eng-Tips staff will check this out and take appropriate action.
Reply To This Thread
Posting in the Eng-Tips forums is a member-only feature.
When was the last time you drove down the highway without seeing a commercial truck hauling goods?The ubiquity of these machines underscores the important roll they play in modern commerce. Download Now