Multi Ratio Current Transformer  CT
Multi Ratio Current Transformer  CT
(OP)
Hi;
What would be the standard ratios for a CT Multi Ratio CT4000/5
Thanks,
DMA
What would be the standard ratios for a CT Multi Ratio CT4000/5
Thanks,
DMA
INTELLIGENT WORK FORUMS
FOR ENGINEERING PROFESSIONALS Member LoginCome Join Us!Are you an
Engineering professional? Join EngTips Forums!
*EngTips's functionality depends on members receiving email. By joining you are opting in to receive email.
Posting GuidelinesPromoting, selling, recruiting, coursework and thesis posting is forbidden.
Link To This Forum! 
Home >
Forums >
Electrical / Electronic Engineers >
Activities >
Electric power & transmission & distribution Forum
Multi Ratio Current Transformer  CT

Multi Ratio Current Transformer  CTMulti Ratio Current Transformer  CT(OP)
Hi;
What would be the standard ratios for a CT Multi Ratio CT4000/5 Thanks, DMA Reply To This ThreadPosting in the EngTips forums is a memberonly feature.Click Here to join EngTips and talk with other members! 
Related NewsResourcesKeeping up with the demand for better, faster design flow performance while preserving the original layout hierarchy of a design can be very challenging during design verification. Download Now
Top performing companies donâ€™t just integrate PLM with their enterprise systems â€“ they also integrate PLM with their engineering tools and CAD systems. Download Now
Radial wheels can match production floor demands where debris or contaminates are present Download Now
Traditional slewing ring bearings are commonplace in wind turbines and heavy industries such as military and construction. Download Now

Join your peers on the Internet's largest technical engineering professional community.
It's easy to join and it's free.
Here's Why Members Love EngTips Forums:
Register now while it's still free!
Already a member? Close this window and log in.
RE: Multi Ratio Current Transformer  CT
RE: Multi Ratio Current Transformer  CT
I don't remember the tap combinations off the top of my head :)
RE: Multi Ratio Current Transformer  CT
600:5
X1:X2 20 turns x 5 = 100:5
X2:X3 10 turns x 5 = 50:5
X3:X4 50 turns x 5 = 250:5
X4:X5 40 turns x 5 = 200:5
1200:5
X1:X2 40 turns x 5 = 200:5
X2:X3 20 turns x 5 = 100:5
X3:X4 100 turns x 5 = 500:5
X4:X5 80 turns x 5 = 400:5
2000:5
X1:X2 80 turns x 5 = 400:5
X2:X3 160 turns x 5 = 800:5
X3:X4 60 turns x 5 = 300:5
X4:X5 100 turns x 5 = 500:5
3000:5
X1:X2 200 turns x 5 = 1000:5
X2:X3 240 turns x 5 = 1200:5
X3:X4 60 turns x 5 = 300:5
X4:X5 100 turns x 5 = 500:5
4000:5
X1:X2 100 turns x 5 = 500:5
X2:X3 300 turns x 5 = 1500:5
X3:X4 200 turns x 5 = 1000:5
X4:X5 200 turns x 5 = 1000:5
5000:
X1:X2 300 turns x 5 = 1500:5
X2:X3 100 turns x 5 = 500:5
X3:X4 400 turns x 5 = 2000:5
X4:X5 200 turns x 5 = 1000:5
RE: Multi Ratio Current Transformer  CT
ie is it the standard to have P1 nearest to the source ?
RE: Multi Ratio Current Transformer  CT
RE: Multi Ratio Current Transformer  CT
RE: Multi Ratio Current Transformer  CT
RE: Multi Ratio Current Transformer  CT
RE: Multi Ratio Current Transformer  CT
Thanks,
Richard Byrne.
Richard Byrne, E.E.T.
RE: Multi Ratio Current Transformer  CT
RE: Multi Ratio Current Transformer  CT