I have noticed that all manufactures of equipment (Trane, Carrier, York) have no power exhaust on side discharge units. I have a 3 unit heat pump system with 15 tons each (2 units will be running at a time, 1 backup). The system max cfm is 12000 cfm (6000cfm/unit), existing exhaust fan for bathrooms, closets, etc is 2000 cfm. If one Heat pump is running i sized one fan for 4000 cfm (6000cfm -2000cfm), and another at 10,000 cfm (12,000cfm-2000). Should I size exhaust fans smaller and let a slight build up in pressure? Is there a rule of thumb for power exhaust units? I noticed that many manufactures use about 1/3 to 1/2 inlet amount to size power exhausts. i.e. 8000 cfm inlet, 4000 cfm power exhaust. Are there any exhaust fans that have 2 speed, that can be controlled by control unit without VAV drive?
Red Flag Submitted
Thank you for helping keep Eng-Tips Forums free from inappropriate posts. The Eng-Tips staff will check this out and take appropriate action.
Reply To This Thread
Posting in the Eng-Tips forums is a member-only feature.
A number of terms like “digitization”, “digital twin”, and “digital thread” have started to emerge in the product design world. While these terms have loose and varying definitions, the core ideas that underpin each of these concepts are becoming increasingly important to successful product development. Download Now
Over the past few years, there has been growing interest among industrial companies and solutions providers with regards to Product Innovation Platforms, where design, manufacturing and IoT tools are bundled into a single software package. Download Now