I have a application which requires the upstream tap of a delta pressure transmitter to be purged with water to help eliminate impulse line plugging. The request is to purge the impulse line with about 1 gpm of process water. The question is "How would this best be accomplished and how will it affect the transmitter calibration?" The taps for the transmitter are across a 16" butterfly valve. I currently have Nitrogen purges on both taps but only the high side tap plugs at this time. Soliciting all inputs as to how to make this work.
Red Flag Submitted
Thank you for helping keep Eng-Tips Forums free from inappropriate posts. The Eng-Tips staff will check this out and take appropriate action.
Reply To This Thread
Posting in the Eng-Tips forums is a member-only feature.