Could anyone tell me the calculation to work out the cooling load for a chiller on an AHU. The flow rate I've been given is 9m3s and a delta T of 10 degC from 25 down to 15 degC. I know with water we use Q=m.c.dT where m is the flow rate in l/hr and we normally use '1' for 'c' assuming it is water. By the way Q is the load in k/cals/hr. We then convert back to kW by dividing by 860.
I'm not sure if the same formula applies and if so, do I need to convert the 9m3s to m3h?
Please help. I'm under pressure for an answer.
Red Flag Submitted
Thank you for helping keep Eng-Tips Forums free from inappropriate posts. The Eng-Tips staff will check this out and take appropriate action.
Reply To This Thread
Posting in the Eng-Tips forums is a member-only feature.
More and more manufacturers are getting into the Industrial Internet of things (IIoT). Those that succeed early in the IIoT arena can be leaders in their market, or solidify their position. Download Now