Could anyone tell me the calculation to work out the cooling load for a chiller on an AHU. The flow rate I've been given is 9m3s and a delta T of 10 degC from 25 down to 15 degC. I know with water we use Q=m.c.dT where m is the flow rate in l/hr and we normally use '1' for 'c' assuming it is water. By the way Q is the load in k/cals/hr. We then convert back to kW by dividing by 860.
I'm not sure if the same formula applies and if so, do I need to convert the 9m3s to m3h?
Please help. I'm under pressure for an answer.
Red Flag Submitted
Thank you for helping keep Eng-Tips Forums free from inappropriate posts. The Eng-Tips staff will check this out and take appropriate action.
Reply To This Thread
Posting in the Eng-Tips forums is a member-only feature.
PCB design is a purposeful process. In essence, every PCB design is a complex puzzle that requires a designer to incorporate critical components and tight schematics into a piece of technology that is governed by rules, constraints and industry standards. Download Now