## 3 Phase motor efficiency calculation

## 3 Phase motor efficiency calculation

(OP)

Hi

Can I calculate the efficiency of a 3 phase motor using the formula W= ?3 x V x I x PF x efficiency.

I have the Input power=1600 Watts, Input Voltage=460 Volts, Rated Current= 2.6 Amps and the Power Factor=0.85. Can I use the values to calculate the efficiency?

Looking forward to the reply

Regards

KShora

Can I calculate the efficiency of a 3 phase motor using the formula W= ?3 x V x I x PF x efficiency.

I have the Input power=1600 Watts, Input Voltage=460 Volts, Rated Current= 2.6 Amps and the Power Factor=0.85. Can I use the values to calculate the efficiency?

Looking forward to the reply

Regards

KShora

## RE: 3 Phase motor efficiency calculation

Po(power out)

Pi(power in)

E=Po/Pi

thus, if you have the rating of the power delivered you just divide it and get your efficiency

OR can use the following

E=(746*HP)/[(746*HP)+(watts lost)] Where 746 is a constant and HP=horsepower

just my two humble cents, hope this helps

Regards

## RE: 3 Phase motor efficiency calculation

Your input power of 1600 W doesn't match the current, voltage, and power factor data you gave. That comes out to 1760 kW.

## RE: 3 Phase motor efficiency calculation

I don't have the Watt Loss data.

Does the equation I posted earlier make sense or not?

Regards

## RE: 3 Phase motor efficiency calculation

Gunnar Englund

www.gke.org

--------------------------------------

100 % recycled posting: Electrons, ideas, finger-tips have been used over and over again...

## RE: 3 Phase motor efficiency calculation

The power value that I have mentioned is written on the motor name plate, I suppose you are correct, it should be called as Output power.

Am I correct?

Regards

## RE: 3 Phase motor efficiency calculation

## RE: 3 Phase motor efficiency calculation

Regards

## RE: 3 Phase motor efficiency calculation

In case you have been waiting for someone to state this more directly, I believe that the posts above confirm that you calculate input power using W = sqrt(3) X V X I X PF and Efficiency = output Power / input Power. We assume that the 1600 Watts marked on the nameplate is output power and efficiency = 91%.

## RE: 3 Phase motor efficiency calculation

You may refer to IEEE Std 112-1996 IEEE Standard Test Procedure for Polyphase Induction Motors and Generators. Or you may refer to the ieee colorbook.

Or you may try this:

"ProMot, a decision support tool, is being developed within the framework of a project cofinanced by SAVE, aiming to aid end-users to explore the possibility of energy savings, in motor systems of an industrial or tertiary installation: electric motors, pumps, compressed air system and chillers. The tool helps in auditing an installation and performing simple meaningful calculations of purchasing, replacing existing or retrofitting electric motor systems. These technical and economic calculations are based on equipment data retrieved from widely accepted and regularly updated European databases and methodologies."

Download at this link,

http://promot.cres.gr/promot_plone/downloads/tools

Regards,

bill

## RE: 3 Phase motor efficiency calculation

Power in = SQRT(3)*V*I*PF = 1.732*460*2.6*0.85 = 1760.8 Watts

Power out (on the shaft) = 1600 Watts (per nameplate data)

EFF = Pout/Pin = 1600/1760 = 0.9086 pu

And the total motor losses = Pin-Pout = 160.8 Watts