I could use a bit of help trying to understand the code requirement for fire dampers at shaft walls. I was reviewing a building air system design that includes a duct riser that extends from the roof down three floors. The shaft wall is noted as 1-hour rating (as expected). I understand in a fully sprinklered building, ducts that penetrate 1-hour walls do not require smoke dampers. Is the same true for shaft walls? I looked through NFPA 90A, but I could not seem to get a clear answer (the diagram does not provide any insight). Perhaps I am overlooking the obvious. Any assistance you can provide is greatly appreciated. Thank you.
Red Flag Submitted
Thank you for helping keep Eng-Tips Forums free from inappropriate posts. The Eng-Tips staff will check this out and take appropriate action.
Reply To This Thread
Posting in the Eng-Tips forums is a member-only feature.