I could use a bit of help trying to understand the code requirement for fire dampers at shaft walls. I was reviewing a building air system design that includes a duct riser that extends from the roof down three floors. The shaft wall is noted as 1-hour rating (as expected). I understand in a fully sprinklered building, ducts that penetrate 1-hour walls do not require smoke dampers. Is the same true for shaft walls? I looked through NFPA 90A, but I could not seem to get a clear answer (the diagram does not provide any insight). Perhaps I am overlooking the obvious. Any assistance you can provide is greatly appreciated. Thank you.
Red Flag Submitted
Thank you for helping keep Eng-Tips Forums free from inappropriate posts. The Eng-Tips staff will check this out and take appropriate action.
Reply To This Thread
Posting in the Eng-Tips forums is a member-only feature.
In a typical integrated circuit (IC) design firm, semi-custom design flows are used to ensure that the final manufactured products meet all of their design requirements and can be delivered on schedule. Download Now
A number of terms like “digitization”, “digital twin”, and “digital thread” have started to emerge in the product design world. While these terms have loose and varying definitions, the core ideas that underpin each of these concepts are becoming increasingly important to successful product development. Download Now