I'm in the process of expanding the electrical distribution system of an existing Healthcare facility. The expansion will consist of a new building that will house Medium Voltage (12.47 kV) switchgear, parallel connected generators (2 new and 1 future), and utility paralleling switchgear. The generators will be rated 12.47 kV, 2250 kW. My experience with 12.47 kV, paralleled generators is limited although the research I have done tells me that I should employ neutral grounding resistors (NGRs) or some other ground fault limiting devices on the generators. Would someone be so kind as to answer the following questions?
1. Is it best to employ one resistor for the system or individual resistors for each generator? The future generator will not be installed initially and the size of the third generator is not yet known due to unforeseen future load conditions.
2. What impact does utility paralleling have on sizing the resistors?
3. What other methods of limiting fault current (if any) might be more suitable or cost effiective?
Your assistance is much appreciated!
Red Flag Submitted
Thank you for helping keep Eng-Tips Forums free from inappropriate posts. The Eng-Tips staff will check this out and take appropriate action.
Reply To This Thread
Posting in the Eng-Tips forums is a member-only feature.
3D printing has opened new doors to rapid prototyping and even rapid production, providing users with the unprecedented ability to visualize products before mass manufacturing and create new designs that could not be made by any other method. Download Now
Ensuring that product lifecycle stakeholders throughout your organization can access the most accurate, up-to-date product information will benefit all aspects of both the product and the organization itself. Download Now
Since the IEEE 802.3bj 100 Gb/s Backplane Ethernet standard has been officially approved, Channel Operating Margin (COM) will likely become an important quality-evaluation method for SERDES links. Download Now