We're having a discussion about requirements for lift levers on RVs. ASME BPVC Sec VIII Div 1 para UG-136(a)(3) states "Each pressure relief valve on air, water over 140°F (60”C), or steam service shall have a substantial lifting device . . .". We interpret the "air" fluid as being ambient air with potential high humidity, and condensate in an air receiver tank. Our service is research air, filtered and dried to a -90F dewpoint. We have never lifted lift levers in our system; we remove RVs and bench test periodically either in-house, or at a VR shop for Code valves. Lift levers make valves expensive. I noted in an API RP520 task force meeting (4/20/2005) that "Nobody in room understands the technical justification for the lifting levers. " Since we are testing valves on the unit or on the bench (per NBIC 23, RB3550), should we require lifting levers?
Red Flag Submitted
Thank you for helping keep Eng-Tips Forums free from inappropriate posts. The Eng-Tips staff will check this out and take appropriate action.
Reply To This Thread
Posting in the Eng-Tips forums is a member-only feature.
More and more manufacturers are getting into the Industrial Internet of things (IIoT). Those that succeed early in the IIoT arena can be leaders in their market, or solidify their position. Download Now