Given a generator 1.6MW 480Y/277V 60Hz and a GSU transformer with primary and secondary windings wye connected, neutral internally tied and solidly grounded. What is the best method of grounding and minimum protection (relaying) necessary for the generator?
Red Flag Submitted
Thank you for helping keep Eng-Tips Forums free from inappropriate posts. The Eng-Tips staff will check this out and take appropriate action.
Reply To This Thread
Posting in the Eng-Tips forums is a member-only feature.
Designers in every industry are being pushed to produce larger and more complex product assembles. Add to that the demands that new software features place on your hardware, and you can be in for some serious performance issues. Download Now