×
INTELLIGENT WORK FORUMS
FOR ENGINEERING PROFESSIONALS

Are you an
Engineering professional?
Join Eng-Tips Forums!
• Talk With Other Members
• Be Notified Of Responses
• Keyword Search
Favorite Forums
• Automated Signatures
• Best Of All, It's Free!

*Eng-Tips's functionality depends on members receiving e-mail. By joining you are opting in to receive e-mail.

#### Posting Guidelines

Promoting, selling, recruiting, coursework and thesis posting is forbidden.

# Voltage Drop Calculation for MV cable

## Voltage Drop Calculation for MV cable

(OP)
Will someone be able to show me how to calculate voltage drop on the medium voltage cable (i.e 11 miles of 350 Kcmil 15 KV EPR cable with 133% insulation to support 150A Load at 13,200 volt)?  There are plenty of calculations available for low voltage system.

### RE: Voltage Drop Calculation for MV cable

Basic method is no different. It is still I/Z. Cable manufacture should be able to provide you with the reactance and resistance values of the cable and use those values. VD=I(R+jX). Use per phase values. I is the line current, VD will be L-N, regardless of the system configuration.

If you have a software, use that.

### RE: Voltage Drop Calculation for MV cable

For 11 miles of 15 kV cable, you may want to also consider the capacitive reactance of the cable and resulting charging current.  This is generally neglected in low voltage calculations, but could be of interest in 11 miles of cable.  For 150A of load (what pf?), the charging current may not be too critical, but becomes more important as the cable gets longer and longer.

You would need a cable model that includes appropriate shunt capacitance in addition to the series inductance and resistance.

### RE: Voltage Drop Calculation for MV cable

To get precise values of voltage drop you have also to take into consideration the ground temperature, which has an influence on the cable resistance.

#### Red Flag This Post

Please let us know here why this post is inappropriate. Reasons such as off-topic, duplicates, flames, illegal, vulgar, or students posting their homework.

#### Red Flag Submitted

Thank you for helping keep Eng-Tips Forums free from inappropriate posts.
The Eng-Tips staff will check this out and take appropriate action.

Close Box

# Join Eng-Tips® Today!

Join your peers on the Internet's largest technical engineering professional community.
It's easy to join and it's free.

Here's Why Members Love Eng-Tips Forums:

• Talk To Other Members
• Notification Of Responses To Questions
• Favorite Forums One Click Access
• Keyword Search Of All Posts, And More...

Register now while it's still free!