Does anyone know if NFPA states that newly constructed fire mains that serve sprinklered buildings or private on-site fire hydrants need to be disinfected (chlorinated) before put into service? Case in point, I have 10 projects in Southern California that the contractor wants to know if he needs to disinfect on the private side of the double check detector device. He has disinfected between the public water main up to the backflow device. Thanks in advance!
Red Flag Submitted
Thank you for helping keep Eng-Tips Forums free from inappropriate posts. The Eng-Tips staff will check this out and take appropriate action.
Reply To This Thread
Posting in the Eng-Tips forums is a member-only feature.
More and more manufacturers are getting into the Industrial Internet of things (IIoT). Those that succeed early in the IIoT arena can be leaders in their market, or solidify their position. Download Now