Does anyone know if NFPA states that newly constructed fire mains that serve sprinklered buildings or private on-site fire hydrants need to be disinfected (chlorinated) before put into service? Case in point, I have 10 projects in Southern California that the contractor wants to know if he needs to disinfect on the private side of the double check detector device. He has disinfected between the public water main up to the backflow device. Thanks in advance!
Red Flag Submitted
Thank you for helping keep Eng-Tips Forums free from inappropriate posts. The Eng-Tips staff will check this out and take appropriate action.
Reply To This Thread
Posting in the Eng-Tips forums is a member-only feature.
Virtual reality (VR) has been around longer than you might think—more than half a century—but it’s only in the last few years that we’ve seen companies and researchers explore its practical applications for manufacturing. Download Now