Does anyone know if the Uniform Codes (UBC, UFC, UMC, etc) or NFPA 72 requires shutdown of all HVAC systems bringing outside air into an area on activation of the alarm system, either by the sprinkler flow switch or an area smoke detector? We have a large open office area (cubicles) served by a dozen rooftop air conditioning units.
Our fire alarm contractor insists that the code requires shutdown of all the HVAC units on activation of the building fire alarm.
Comments please. Thanks
Red Flag Submitted
Thank you for helping keep Eng-Tips Forums free from inappropriate posts. The Eng-Tips staff will check this out and take appropriate action.
Reply To This Thread
Posting in the Eng-Tips forums is a member-only feature.
PCB design is a purposeful process. In essence, every PCB design is a complex puzzle that requires a designer to incorporate critical components and tight schematics into a piece of technology that is governed by rules, constraints and industry standards. Download Now