Its known that in a positive displacement pump suction line must be take in account the acceleration head (ha)and substract it for the NPSHA. But, what is the value of NPSHA for comparison with NPSHR. NPSHA = Pa+Hs-Pv-hf-ha? or NPSHA = Pa+Hs-Pv-hf? Why? Thanks
Red Flag Submitted
Thank you for helping keep Eng-Tips Forums free from inappropriate posts. The Eng-Tips staff will check this out and take appropriate action.
Reply To This Thread
Posting in the Eng-Tips forums is a member-only feature.
Version control is neither a new concept or a new software feature. But with the explosion of digital information, thereâ€™s an even greater need for tight control and management of documents and data. Download Now