I have a current imbalance in a three phase chiller motor (480v 300 hp)Each phase: 1- 200 2 - 215 3 - 252. The voltage imbalance for this is less than three percent. We are also seeing other motors in the facility experiencing current imbalance. We also see the power factor readings for each leg can be more than 1o percent diffeent. If one motor suffered current imbalance I would suspect a motor problem but five tend to lead to a distribution problem. Is it possible several nonlinear loads (277 lighting, etc.) can be a contributing factor?
Red Flag Submitted
Thank you for helping keep Eng-Tips Forums free from inappropriate posts. The Eng-Tips staff will check this out and take appropriate action.
Reply To This Thread
Posting in the Eng-Tips forums is a member-only feature.
Current integrated circuit (IC) designs are complex, which can result in different voltages being located close to one another. To prevent time dependent dielectric breakdown (TTDB), it is essential to incorporate space rules within IC design. Download Now
3D printing offers the ability to manufacture complex geometries, custom components on-demand and batches of short-run parts. However, with a new fabrication method comes new design principles. Download Now