INTELLIGENT WORK FORUMS
FOR ENGINEERING PROFESSIONALS
Come Join Us!
Are you an
Join Eng-Tips Forums!
- Talk With Other Members
- Be Notified Of Responses
To Your Posts
- Keyword Search
- One-Click Access To Your
- Automated Signatures
On Your Posts
- Best Of All, It's Free!
*Eng-Tips's functionality depends on members receiving e-mail. By joining you are opting in to receive e-mail.
Promoting, selling, recruiting, coursework and thesis posting is forbidden.
Electric motors & generators engineering FAQ
How to check a motor (AC) if it is faulty or not?
Posted: 3 Aug 00
How do you know a motor is ok or not? How do you have a preliminary idea about a non-functioning/ malfunctioning motor? Especially, if you don't want to remove the motor from its mounting?
There are a couple of preliminary tests you could do.
First, try finding the ground resistence of the motor. Put the multi-meter in kilo-ohms and check the resistence between the motor body(or your metallic connector box) and the terminals of the motor. It should show a fairly high value- could be 100 K-ohms or above. Else, there is a ground leakage- this is probably the reason why you get shock (if you're getting!).
Next, you could find the resistance of the winding. Connect between the terminals. (I don't know the type of motor used). Across the motor windings you should get a low finite value- could be a couple of hundred ohms- or less.
Both the ohm values depend on the rating and type of the motor. What I've specified are indicative only. For example, for a large motor, the winding resistance could be tens ohms or less. For smaller motors, it could be a hundred ohms or so.
Now, you have to go to the motor!
I feel it is always better to check the motor at the winding terminals rather than the cable end. Ideally, this should not matter- but take into consideration the working environment - if it's moist and salty, I guess there is a probability that the insulation can become bad, and over many feet of cable length, there could be so much leakage if the cabling is old.
I've come across many instances where there is a cable fault. So, if there is a bad cable, we may be suspecting that the poor motor is guilty if we don't check the motor at the winding terminals.
Hence what we usually do is:
1. Disconnect the conductors from the drive control end, and megger between cables and each cable to ground. Between cables, it should give almost equal value, in the range of 1-3 ohms for medium rating motors and higher for smaller motors. Between each conductor and ground, megger value should be relatively high, above 100 Kohms or above. (More exact values will be specified by the manufacturer; it will also depend on the working environment and type of motor enclosure)
2. If there is any problem, go to the motor, disconnect the cable - thus isolate the motor- and check the motor terminals again. Now, we can identify the problem to either the cable or the motor.
Back to Electric motors & generators engineering FAQ Index
Back to Electric motors & generators engineering Forum
The Internet of Things (IoT) boom is increasing the demand for Analog mixed-signal (AMS) integrated circuits (IC). Download Now
3D printing has opened new doors to rapid prototyping and even rapid production, providing users with the unprecedented ability to visualize products before mass manufacturing and create new designs that could not be made by any other method. Download Now
Ensuring that product lifecycle stakeholders throughout your organization can access the most accurate, up-to-date product information will benefit all aspects of both the product and the organization itself. Download Now
Since the IEEE 802.3bj 100 Gb/s Backplane Ethernet standard has been officially approved, Channel Operating Margin (COM) will likely become an important quality-evaluation method for SERDES links. Download Now
Join Eng-Tips® Today!
Join your peers on the Internet's largest technical engineering professional community.
It's easy to join and it's free.
Here's Why Members Love Eng-Tips Forums:
- Talk To Other Members
- Notification Of Responses To Questions
- Favorite Forums One Click Access
- Keyword Search Of All Posts, And More...
Register now while it's still free!
Already a member? Close this window and log in.
Join Us Close