INTELLIGENT WORK FORUMS
FOR ENGINEERING PROFESSIONALS
Come Join Us!
Are you an
Join Eng-Tips Forums!
- Talk With Other Members
- Be Notified Of Responses
To Your Posts
- Keyword Search
- One-Click Access To Your
- Automated Signatures
On Your Posts
- Best Of All, It's Free!
*Eng-Tips's functionality depends on members receiving e-mail. By joining you are opting in to receive e-mail.
Promoting, selling, recruiting, coursework and thesis posting is forbidden.
Electric motors, generators & controls engineering FAQ
Overload Trip Class - What does it really mean?
Posted: 1 Jul 03
Quite often we here of applications in which the motor protection/overload relay 'trips' during normal motor starting. The remedial action taken by many when faced with this problem is to select and install a replacement overload relay, generally one that provides a higher 'Trip Class' setting, for example, Trip Class 20 in lieu of the standard Trip Class 10.
Note: There appears to be a general misconception in industry that Overload Trip Class relates directly to the starting time of a machine. This is not the case!
All due care must be taken when selecting a protection relay offering higher Trip Class, as this can result in under protection and subsequent failure of the motor.
To select an overload relay with a more suitable trip class, you must in the first instance obtain data relating to the motorÆs thermal withstand capabilities. For example, you need to know how many seconds (from cold condition) the motor can the sustain Locked Rotor Current before it is compromised.
This information is readily available from most leading manufacturers of motors and is generally provided in one of two formats.
a) Specific values for Locked Rotor Current and maximum Locked Rotor Time (from 'cold condition' ) are given.
b) A Motor Thermal Withstand Curve is provided.
With this information available to you, you can refer to the tables given in IEC 60947 to identify the most appropriate Overload Trip Class. This is defined as the one that provides a trip curve as close as possible to but below the overload curve of the motor. Adopting this process will ensure nuisance tripping is minimised and that the motor is adequately protected at all times.
Note: If the above processes are adopted but the trip conditions continue, there are 4 possible causes.
1. The motor (and overload relay) are not given sufficient time to cool between starts.
2. Assuming reduced voltage start (star/delta, auto-transformer, primary resistance, soft start etc., the motor is not delivering torque sufficient to accelerate the connected load to speed. That is the starting current and starting time under RVS conditions exceeds that permissible by the overload curve.
3. A more advanced protection strategy such as motor thermal modelling may be required. Motor thermal modelling allows the user to 'match' the curves of the protection device to the connected motor. This is of particular advantage when the motors thermal withstand capabilities and the start condition (starting current and starting time) fall between two curves defined by standard overload trip classes.
4. The motor is simply too small for the application.
Put simply, the most appropriate protection strategy is the one that allows the motor to be fully utilised without nuisance tripping or fear of motor burn-out.
Back to Electric motors, generators & controls engineering FAQ Index
Back to Electric motors, generators & controls engineering Forum
Keeping up with the demand for better, faster design flow performance while preserving the original layout hierarchy of a design can be very challenging during design verification. Download Now
Top performing companies donâ€™t just integrate PLM with their enterprise systems â€“ they also integrate PLM with their engineering tools and CAD systems. Download Now
Radial wheels can match production floor demands where debris or contaminates are present Download Now
Traditional slewing ring bearings are commonplace in wind turbines and heavy industries such as military and construction. Download Now
Join Eng-Tips® Today!
Join your peers on the Internet's largest technical engineering professional community.
It's easy to join and it's free.
Here's Why Members Love Eng-Tips Forums:
- Talk To Other Members
- Notification Of Responses To Questions
- Favorite Forums One Click Access
- Keyword Search Of All Posts, And More...
Register now while it's still free!
Already a member? Close this window and log in.
Join Us Close