INTELLIGENT WORK FORUMS
FOR ENGINEERING PROFESSIONALS
Come Join Us!
Are you an
Join Eng-Tips Forums!
- Talk With Other Members
- Be Notified Of Responses
To Your Posts
- Keyword Search
- One-Click Access To Your
- Automated Signatures
On Your Posts
- Best Of All, It's Free!
*Eng-Tips's functionality depends on members receiving e-mail. By joining you are opting in to receive e-mail.
Promoting, selling, recruiting, coursework and thesis posting is forbidden.
Electric power & transmission & distribution FAQ
Electric Power Engineering
Very Brief Overview of Symmetrical Components (positive, negative, & zero sequence)
Posted: 23 Jul 02
Reference Protective Relaying Principles and Applications by J. Lewis Blackburn.
Considering a three-phase system, symmetrical components (positive sequence, negative sequence, and zero sequence) allow one to analyze power system operation during unbalanced conditions such as those caused by faults between phases and/or ground, open phases, unbalanced impedances, and so on. The positive sequence set consists of the balanced three-phase currents and line-to-neutral voltages supplied by the system generator. They are always equal in magnitude and phase displaced by 120 degrees rotating at the system frequency with a phase sequence of normally a, b, c. The sequence currents or sequence voltages always exist in three's, never alone or in pairs.
The negative sequence set is also balanced with three equal magnitude quantities at 120 degrees apart but with the phase rotation or sequence reversed, or a, c, b. (If the positive sequence is a, c, b as in some power systems, then negative sequence will be a, b, c.) For the negative sequence set, again the sequence currents or sequence voltages always exist in three's, never alone or in pairs.
The members of the zero-sequence set of rotating phasors are always equal in magnitude and always in phase. Once again, if zero sequence currents or zero sequence voltages exist, they must exist in all three phases, never alone or in one phase.
In transformers, lines, etc., the phase sequence of the current does not change the impedance encountered, so positive sequence impedance equals negative sequence impedance; X1 = X2. System generators do not generate negative sequence currents, but negative sequence can flow in their windings. For rotating machines X2 = 1/2(X"d + X"q). Except for calculating faults very near machine terminals, can assume X"d=X"q, so X2 = X"d.
Zero sequence for transformers is equal to the positive & negative sequence and is the transformer leakage impedance, except in core-type transformers where Xo = .85 to .9 times X1. For estimating open lines Xo = 3 or 3.5 times X1 is commonly used. Zero sequence impedance of generators is low and variable depending on winding design.
Back to Electric power & transmission & distribution FAQ Index
Back to Electric power & transmission & distribution Forum
There is proven benefit for product development teams in using an integrated design and data management system.
However, not all product teams can afford, need or want all the various modules in an enterprise PLM system.
Rapid prototyping has become a game-changing innovation for designers, engineers and manufacturers. Previously, the process of creating wood or metal prototypes took weeks or months and the cost was often so prohibitive that designers skipped prototypes entirely and went directly from CAD to tooling. Download Now
This white paper provides a comprehensive overview of parylene conformal coating, the advantages of parylene and applications for parylene to protect electronic devices.
Companies expect a lot of savings when they move their applications to the cloud, but these savings arenâ€™t a slam-dunk. Download Now