×
INTELLIGENT WORK FORUMS
FOR ENGINEERING PROFESSIONALS

Are you an
Engineering professional?
Join Eng-Tips Forums!
• Talk With Other Members
• Be Notified Of Responses
• Keyword Search
Favorite Forums
• Automated Signatures
• Best Of All, It's Free!

*Eng-Tips's functionality depends on members receiving e-mail. By joining you are opting in to receive e-mail.

#### Posting Guidelines

Promoting, selling, recruiting, coursework and thesis posting is forbidden.

# Pipelines, Piping and Fluid Mechanics engineering FAQ

## Flow in Pipe

 When should I segment my pipeline flow calculations? by zdas04 faq378-1933 Posted: 28 May 16 It has always been an article of faith that if the density of the downstream piping were within 10% of the density of the upstream piping then the incompressible flow equations would provide adequate results in an inherently compressible fluid. When the downstream density is less than 90% of the upstream density then common practice was to segment the line until that 90% was realized. To get a feel for how valid this assumption is I wrote a MathCad program to bust up a flow problem with downstream density around 50% of upstream density for a single segment and then matched the (pipeline inlet - pipeline outlet) dP while segmenting the line finer and finer. Assumptions: 100% CH4 (MW 16.043, SG 0.5539)Std weight 24 inch new steel pipe (ID 23.25 in, efficiency 0.95, absolute roughness 150E-06 ft)No water standing in lineTemp constant at 520RUpstream pressure 580 psia [40 bara]Downstream pressure 290 psia [20 bara]Line length 62 mi [100 km]Steps: Guess segment downstream pressureCalculate average pressure with the guess (using front-end loaded average)Calculate compressibility at average and standard pressureCalculate density at average pressure and standard pressureCalculate viscosity at average pressureCalculate Reynolds NumberCalculate Fanning Friction FactorUsing Isothermal Gas Flow Equation to calculate downstream pressureIf calculated downstream pressure more than 100 Pa from guess, iterate 1-9.Move segment downstream pressure to upstream pressure and repeat 1-10I ran the program for a number of different segments: Seg Length...........Max Flow rate..........Density Ratio (worst segment) 100 km.................243.725 MMSCF/day...............48.1% 50 km..................243.759 MMSCF/day...............61.5% 25 km..................243.759 MMSCF/day...............74.3% 10 km..................243.759 MMSCF/day...............87.0% 2 km...................243.765 MMSCF/day...............96.9% 1 km...................243.765 MMSCF/day...............98.4% 500 m..................243.765 MMSCF/day...............99.2% 250 m..................243.765 MMSCF/day...............99.6% 100 m..................243.765 MMSCF/day...............99.8% 10 m...................243.765 MMSCF/day...............99.9+% I found it interesting that above 90% the flow rate was unchanging. I re-ran this several times for flow rates increasing and found that below 90%, the flow rate changed with increasing segmentation, and above 90% a given dP gave the same flow rate. Changes above 30% were pretty small (more than the 0.016% above, but much smaller than the +/-10% accuracy we expect to get from this equation). My conclusion is that I will continue to use the 90% check, but certainly understand why someone would ignore it for pipeline calculations. Back to Pipelines, Piping and Fluid Mechanics engineering FAQ Index Back to Pipelines, Piping and Fluid Mechanics engineering Forum

Close Box

# Join Eng-Tips® Today!

Join your peers on the Internet's largest technical engineering professional community.
It's easy to join and it's free.

Here's Why Members Love Eng-Tips Forums:

• Talk To Other Members
• Notification Of Responses To Questions
• Favorite Forums One Click Access
• Keyword Search Of All Posts, And More...

Register now while it's still free!