INTELLIGENT WORK FORUMS
FOR ENGINEERING PROFESSIONALS
Come Join Us!
Are you an
Join Eng-Tips now!
- Talk With Other Members
- Be Notified Of Responses
To Your Posts
- Keyword Search
- One-Click Access To Your
- Automated Signatures
On Your Posts
- Best Of All, It's Free!
*Eng-Tips's functionality depends on members receiving e-mail. By joining you are opting in to receive e-mail.
Promoting, selling, recruiting, coursework and thesis posting is forbidden.
Expansion and flexibility
Pressure increase due to thermal expansion of a trapped liquid
Posted: 25 May 07
The calculation of pressure increase due to thermal expansion of a liquid fully filling, without any gas bubbles or pockets, a metallic enclosure, may be treated as follows.
The phenomena to be considered are:
1)thermal expansion of liquid due to the change of its bulk temperature
2)thermal expansion of the vessel or pipe, assumed in the following as having the same temperature as the fluid
3)compressibility of liquid under the increase in pressure due to the constrained volume
4)increase in volume of the vessel under the increased pressure of the fluid.
The corresponding contributions to the relative change in volume δV/V of fluid or of the containing space may be evaluated as follows:
-αf is the volumetric coefficient of thermal expansion of the fluid
-αv is the volumetric coefficient of thermal expansion of the vessel (= three times the linear one)
-ΔT is the change in temperature
-β is the compressibility factor of the fluid, or the relative change in volume per unit change in pressure
-ΔP is the change in pressure of the fluid (it is what we seek)
-D,t and E are respectively the diameter, the thickness and the elastic modulus of the vessel (or pipe)
By equating the change in volume of the fluid to the change in volume of the vessel one gets:
Let's take as an example water as the entrapped fluid and carbon steel for the container, at temperatures not far from room temperature.
D/t will of course widely vary according to the dimensions and design pressure of the container; we may assume a variation between 100 for a light vessel or pipe and 10 for a quite heavy vessel, the value of 0 corresponding to an infinitely rigid container.
With these figures we get (per degree C of change in temperature):
ΔP=0.19 MPa =~ 2 bar for the light container
ΔP=0.39 MPa =~ 4 bar for the heavy container
ΔP=0.44 MPa =~ 4.4 bar for the rigid container
Back to Pipelines, Piping and Fluid Mechanics engineering FAQ Index
Back to Pipelines, Piping and Fluid Mechanics engineering Forum
Join Eng-Tips® Today!
Join your peers on the Internet's largest technical engineering professional community.
It's easy to join and it's free.
Here's Why Members Love Eng-Tips Forums:
- Talk To Other Members
- Notification Of Responses To Questions
- Favorite Forums One Click Access
- Keyword Search Of All Posts, And More...
Register now while it's still free!
Already a member? Close this window and log in.
Join Us Close